Your community newsletter is now available on the website. To access the prior months/years newsletters, please visit the Newsletter Page.
Please make sure that you complete the 2019 pool registration form. NO ONE will be allowed to enter the pool area without a proximity card and having submitted the pool form. Once you have completed this form, please forward it to the on-site office. The pool monitor will not be able to accept this form nor provide access to the facility.
Additionally, homeowners/renters that have been suspended will not be authorized to utilize the pool, spa and BBQ area.
Attention All Tierra Shores Residents!
Please be aware that there have been quite a number of coyote sightings in and around our neighborhood and this is a notice to remind all to be vigilant, watch out for your fur babies and remove any outside food sources to help alleviate an opportunity for these animals to be attracted to the neighborhood.
Thank you for your cooperation!
The paddle boats will open on October 26, 2019 at 8:30 AM. Please contact the guard service at 909-553-6332 should you wish to use the boats.
Update as of July 24, 2019 at 2:00 a.m. PST
Great news! 😛
The well has been up and running as of Saturday, July 20, 2019.
It will continue to run until the lake is full.
I would like to update you all on the inspection results of the pumping equipment that was recovered from the bottom of the well.
It’s unfortunate to report that there are some problems. The vendor removed the end-cap of the sand perpetrator, and found that it was completely plugged with filter pack, aka gravel. This gravel is what filters the water coming into the well. The presence of this much gravel, is an indicator that a hole may have developed in the well casing, allowing gravel to intrude. It looks as though the pump has been passing gravel as well, this has caused the impeller skirt to wear thin, and break.
A video will need to be performed to see where the gravel may be coming from.
I would also like to inform you that the Board called an emergency meeting yesterday and approved the equipment needing to be replaced as well as the video log.
Please be advised that fishing is closed until further notice due to the water level. We apologize for any inconvenience.
As many of you have noticed, the lake level is dropping. Here is a quick explanation as to what happened. The Certilok pvc coupling broke causing the pump, motor, and some pvc pipe to drop to the bottom of the well. Unfortunately, the paddle boats will be closed until further notice.
The Board is working to resolve this issue in a timely manner. We will continue to make this one of our main priorities and keep you informed.
As of June 7, 2019 the gates will close after each vehicle passes the safety loops. Please wait for gates to open completely before driving through. Damage to gates caused by vehicle will be at the expense of the vehicle owner.